APPLIANCE WIRING MATERIAL
Style 5107 Multiple conductor with other-than-extruded insulation
Rating 200 or 450 deg C, 600 Vac, Horizontal flame.
Conductor 26 AWG – 550 kcmil. Solid or stranded for sizes 26 – 8 AWG; Stranded only for larger sizes than 8 AWG.
Insulation Mica tape with braid, or Mica composite (see Facing Page) with braid.
Conductor size Min average thickness of Mica tape Min average thickness of Glass Braid Treated with Silicone Varnish or TFE Finish
26 – 12 AWG 25 mils 7 mils
11 – 4 AWG 30 mils 15 mils
3 – 4/0 AWG 35 mils 20 mils
250 – 550 kcmil 40 mils 20 mils
Assembly Optional, two or more insulated conductors, may be cabled together with a max O.D. of 1.500 inches. A mica glass binder and/or fiberglass fillers may be employed.
Shield Optional, 36 – 30 AWG strands.
Covering Optional, over assembly, treated glass braid.
Standard Appliance Wiring Material UL 758.
Use Internal Wiring of high-temperature equipment where not subjected to repeated flexing and protected from mechanical abuse, and where the acceptability, including current-carrying capacity, has been determined by Underwriters Laboratories Inc.
UL and the UL Logo are trademarks of UL LLC © 2014