APPLIANCE WIRING MATERIAL
Style 2935 Multiconductor Cable with Extruded Non-Integral Jacket.
Rating 80 deg C, 300 Vac, Cable flame.
Insulation Labeled or complying with manufacturer’s AWM procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional. A 6 mil or heavier PVC covering may be extruded over the conductor assembly.
Jacket Extruded PVC
major dia in inches of 0.700 or less 30 mils min average 24 mils minimum at any point
0.70l-l.000 dia 45 avg 36 min
1.001-1.500 dia 60 avg 48 min
Misc. Fillers – Required if necessary to form a relatively smooth round core for extrusion of outer jacket.
Standard Appliance Wiring Material UL 758.
Use Internal wiring or external wiring.
UL and the UL Logo are trademarks of UL LLC © 2014