APPLIANCE WIRING MATERIAL
Style 2919 Multi-conductor cable with non-integral jacket
Rating 80 deg C, 30 Vac, Cable flame.
Insulated Conductor Labeled or complying with manufacturer’s AWM procedure. 40 AWG minimum.
Assembly Two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. Barrier layers, binders over groups of conductors and/or the complete conductor assembly, and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional. A 6 mil or heavier PVC covering may be extruded over groups of conductors and/or over the complete conductor assembly.
Shield Optional. May be provided over groups of conductors and/or over the complete conductor assembly.
Jacket Extruded PVC.
Diameter of core assembly under jacket* Minimum average thickness Minimum thickness at any point
0.425 inch or less 30 mils 24 mils
0.426-0.700 inch 45 mils 36 mils
0.701-1.000 inch 60 mils 48 mils
1.000-1.500 inch 80 mils 64 mils
1.501-2.500 inch 110 mils 88 mils
2.501 inch and larger 140 mils 112 mils
* – Major diameter if cable is flat or oval.
Standard Appliance Wiring Material UL 758.
Use Internal wiring or external interconnection in Class 2 Circuits of electronic computers and electric business machines.
UL and the UL Logo are trademarks of UL LLC © 2014