APPLIANCE WIRING MATERIAL
Style 2842 Multiple-conductor cable using non-integral jacket.
Rating 80 deg C, 30 Vac, Cable flame.
Insulated Conductor 40 AWG minimum – Labeled or complying with Manufacturer’s AWM Procedure having a minimum rating of 80 deg C.
Assembly Two or more twisted singles or groups of twisted singles cabled together to form a flat or round cable with no more than three rows of single conductors or groups of conductors. Lay not specified. Barrier layer and/or fillers optional. Manufacturer shall maintain a complete description of each assembly.
Jacket Extruded PVC
Diameter of core assembly under jacket Minimum average thickness Minimum thickness at any point
1.0 inch or less 45 mils 36 mils
1.001-1.500 inch 60 mils 48 mils
1.501-2.500 inch 80 mils 64 mils
2.501-4.000 inch 110 mils 88 mils
4.001 inch or larger 140 mils 112 mils
Standard Appliance Wiring Material UL 758.
Use External Interconnection in Class 2 circuits of Electronic Equipment where each end is terminated in connectors.
UL and the UL Logo are trademarks of UL LLC © 2014