APPLIANCE WIRING MATERIAL
Style 2786 Multiple-conductor cable using non-integral jacket.
Rating 60 deg C, Voltage not specified, Horizontal flame.
Insulation Labeled or complying with Manufacturer’s AWM Procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. the conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering (Optional) – A 6 mil or heavier extruded PVC covering may be over the conductor assembly.
Jacket Extruded PVC;
major dia in inches of 0.250 or less 15 mils minimum average thickness 12 mils minimum thickness at any point
0.251-0.700 dia 30 avg 24 min
0.701-1.000 dia 60 avg 48 min
1.001-1.500 dia 80 avg 64 min.
– Major diameter if cable is flat or oval
Standard Appliance Wiring Material UL 758.
Use Internal wiring.
UL and the UL Logo are trademarks of UL LLC © 2014