APPLIANCE WIRING MATERIAL
Style 2655 Multiple-conductor cable using non-integral jacket.
Rating 80 deg C, 300 Vac, Cable flame.
Conductor 36 AWG min – 6 AWG. Copper, copper clad steel, or copper alloy, bare or coated (tin or silver), solid or stranded.
Insulation Labeled or complying with manufacturer’s AWM Procedure.
Assembly Two or more individually insulated conductors or groups of insulated conductors cabled together to form a round cable. A flat or oval cable may also be constructed with no more than three rows of single conductors or groups of conductors. The length of lay of the twisted conductors or groups is not specified. Fillers may be used in a cable but are not required. A barrier layer, if employed, may be a fibrous wrap serving, or braid; paper; nylon; oriented polyethylene terephthalate; or a thermoplastic- tape wrap. Such a barrier layer would serve to protect the cable during further processing, and would be applied immediately over the twisted assembly of individual conductors or groups of conductors.
Jacket Extruded PVC;
dia in inches of 0.700 or less 30 mils minimum average thickness 24 mils minimum thickness at any point
0.701-1.000 dia 45 avg 36 min
1.001-1.500 dia 60 avg 48 min
1.501-2.500 dia 80 avg 64 min
2.501 dia and larger 110 avg 88 min
4.001 dia and larger 140 ave 112 min.
– Major diameter if cable is flat or oval.
Standard Appliance Wiring Material UL 758.
Use External wiring.
UL and the UL Logo are trademarks of UL LLC © 2014