APPLIANCE WIRING MATERIAL
Style 2626 Multiple-conductor cable using non-integral jacket.
Rating 80 deg C, 30 Vac, Cable flame.
Insulation Labeled or complies with manufacturer’s AWM Procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering (Optional) A 6 mil or heavier Extruded PVC covering may be over the conductor assembly.
Jacket Extruded PVC
major dia in inches of 0.425 or less 30 mils minimum average thickness 24 mils minimum thickness at any point
0.426-0.700 dia 45 avg 36 min
0.701-1.000 dia 60 avg 48 min
1.001-1.500 dia 80 avg 64 min
1.501-2.500 dia 110 avg 88 min
2.501 dia and larger 140 avg 112 min.
– Major dia if cable is flat or oval.
Standard Appliance Wiring Material UL 758.
Use Internal wiring or External interconnection in Class 2 Circuits.
UL and the UL Logo are trademarks of UL LLC © 2014