APPLIANCE WIRING MATERIAL
Style 2614 Multiple-Conductor Cable using Non-Integral Jacket
Rating 105 deg C, 30 Vac, Cable flame.
Conductor 40 AWG minimum, solid or stranded.
Insulation Labeled or complying with Manufacturer’s AWM Procedure except that Styles rated 30 Volts for Class 2 operation may not be used.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional. Extruded PVC, a 6 mils or heavier, may be extruded over the conductor assembly.
Jacket Extruded PVC.
Diameter of core assembly under jacket inches Minimum average thickness mils Minimum thickness at any point mils
0.425 or less 30 24
0.426-0.700 45 36
0.701-1.000 60 48
1.001-1.500 80 64
1.501-2.500 110 88
2.501 and larger 140 112
Standard Appliance Wiring Material UL 758.
Use External wiring.
UL and the UL Logo are trademarks of UL LLC © 2014