APPLIANCE WIRING MATERIAL
Style 2587 Multiple-conductor cable using non-integral jacket.
Rating 90 deg C, 600 Vac, Cable flame.
Conductor 40 AWG min, solid or stranded.
Insulation Labeled or complying with Manufacturer’s AWM Procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. May use same or mixed AWG size.
Covering Optional, extruded PVC, a 6 mils or heavier, may be extruded over the conductor assembly.
Jacket Extruded PVC.
Dia of round assembly under jacket inches Minimum average thickness mils Minimum at any point mils
0.700 or less 30 24
0.701-1.000 60 48
1.001-1.500 80 64
1.501-2.500 110 88
Standard Appliance Wiring Material UL 758.
Use External interconnection or internal wiring.
UL and the UL Logo are trademarks of UL LLC © 2014