APPLIANCE WIRING MATERIAL
Style 2586 Multiple-conductor cable using non-integral jacket
Rating 105 deg C, 600 or 1000 Vac, Cable flame.
Conductor 40 AWG minimum.
Insulated Conductor Labeled or complying with manufacturer’s AWM Procedure.
Assembly Two or more conductors or groups of conductors laid parallel or twisted forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. May use same or mixed AWG size.
Covering Optional, Extruded PVC, 6 mils minimum thickness at any point.
Jacket Extruded PVC.
Diameter of cable under jacket* Minimum average thickness Minimum thickness at any point
0.700 inch or less 30 mils 24 mils
0.701-1.000 inch 60 mils 48 mils
1.001-1.501 inch 80 mils 64 mils
1.501-2.500 inch 110 mils 88 mils
* – Major diameter if cable is flat or oval
Standard Appliance Wiring Material UL 758.
Use External interconnection or internal wiring.
UL and the UL Logo are trademarks of UL LLC © 2014