APPLIANCE WIRING MATERIAL
Style 2584 Multi-conductor Cable with Extruded Non-Integral Jacket
Rating 80 deg C, 125 Vac, Cable flame.
Insulated Conductor 40-9 AWG. Labeled or complying with Manufacturer’s AWM Procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional – Extruded PVC, 6 mils minimum thickness.
Jacket Extruded PVC
@Diameter of core assembly under jacket Minimum average thickness Minimum thickness at any point
0.700 inch or less 30 mils 24 mils
0.701 to 1.000 inch 45 mils 36 mils
1.001 to 1.500 inch 60 mils 48 mils
@ – Major dia if cable is flat or oval.
Standard Appliance Wiring Material UL 758.
Use External interconnection or internal wiring of electronic equipment.
UL and the UL Logo are trademarks of UL LLC © 2014