APPLIANCE WIRING MATERIAL
Style 2560 Multiple-conductor cable using non-integral jacket
Rating 60 deg C, 30 Vac, Cable flame.
Insulated Conductor Labeled or complies with manufacturer’s procedure or see Facing Page.
Assembly Two or more singles or groups of singles twisted together. The singles or groups may be either laid parallel to form a flat cable with no more than three rows of single conductors or groups of conductors or cabled together to form a round cable. Barrier layer and/or fillers optional. Manufacturer shall maintain a complete description of each assembly.
Jacket Extruded PVC.
Diameter of flat cable or diameter of round cable under jacket Minimum average thickness Minimum thickness at any point
0.425 inch or less 30 mils 24 mils
0.426 – 0.700 inch 45 mils 36 mils
0.701 – 1.000 inch 60 mils 48 mils
1.001 – 1.500 inch 80 mils 64 mils
1.501 – 2.500 mils 110 mils 88 mils
2.501 inch and larger 140 mils 124 mils
Standard Appliance Wiring Material UL 758.
Use External wiring, Class 2 circuits only.
UL and the UL Logo are trademarks of UL LLC © 2014