APPLIANCE WIRING MATERIAL
Style 2517 Multiple-conductor cable using non-integral jacket
Rating 105 deg C, 300 Vac, Cable Flame.
Insulated Conductor Labeled or complying with Manufacturer’s AWM Procedure. 40 AWG minimum.
Assembly Consists of two or more singles, twisted pairs or groups of twisted singles twisted together. The singles or groups of singles may be laid parallel forming a flat, oval or round cable. The lay of the conductors are not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Jacket Extruded PVC.
Diameter of Core Assembly under [email protected] Minimum Average Thickness Minimum Thickness at any point
0.700 inch or less 30 mils 24 mils
0.701 – 1.000 inch 45 mils 36 mils
1.001 – 1.500 inch 60 mils 48 mils
1.501 – 2.500 inch 80 mils 64 mils
@ – Major diameter if cable is flat or oval.
Covering Optional, braid.
Standard Appliance Wiring Material UL 758.
Use External interconnection of electronic equipment or internal wiring of electronic equipment or appliances. Tags may also indicate the following: “600 Volts peak for Electronic Use Only”.
UL and the UL Logo are trademarks of UL LLC © 2014