APPLIANCE WIRING MATERIAL
Style 2463 Multiple-conductor cable using non-integral jacket
Rating 80 deg C, 600 Vac, Cable flame.
Conductor 40 AWG minimum, solid or stranded.
Insulated Conductor Labeled or complying with Manufacturer’s AWM Procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional, Extruded PVC, 6 mils minimum thickness at any point, over the conductor assembly.
Jacket Extruded PVC.
Diameter of assembly under jacket Construction A – Minimum average thickness Construction A – Minimum thickness at any point Construction B – Minimum average thickness Construction B – Minimum thickness at any point
0.425 inches or less 30 mils 24 mils 45 mils 36 mils
0.425-0.700 inches 60 mils 48 mils 60 mils 48 mils
0.701-1.500 inches 80 mils 64 mils 80 mils 64 mils
Standard Appliance Wiring Material UL 758.
Use Construction A: Internal wiring of X-ray Equipment, or in the internal or exteral interconnection of electronic equipment. Construction B: External interconnection of electronic equipment in abuse areas, such as X-ray Equipment and Business Machines.
UL and the UL Logo are trademarks of UL LLC © 2014