APPLIANCE WIRING MATERIAL
Style 2462 Multiple-conductor cable using non-integral jacket.
Rating 60 deg C, 300 Vac, FT2 flame.
Conductor 24 AWG – 10 AWG, stranded.
Insulation CONSTRUCTION A and C – Extruded PVC, 15 mils minimum average thickness, 13 mils minimum thickness at any point. CONSTRUCTION B – Extruded PVC, 30 mils minimum average thickness, 27 mils minimum thickness at any point.
Assembly CONSTRUCTION A and C – two to seven insulated conductors, same as Type SVT. CONSTRUCTION B – two to nine insulated conductors, same as Type SJT. All construction – Different conductor sizes may be employed in one cord, no polarity identification required.
Shield Optional – One or more of the individually insulated conductors may be shielded or groups of individually insulated conductors may be shielded. Shielding over conductor shall consist of 36 AWG – 30 AWG tinned or untinned copper strands applied as a wrap or braid.
Jacket CONSTRUCTION A and B – Extruded PVC, 30 mils minimum average thickness, 24 mils minimum thickness at any point. Construction C – Extruded PVC.
Diameter of core assembly under jacket Minimum average thickness Minimum thickness at any point
0.700 inch or less 30 mils 24 mils
Standard Appliance Wiring Material UL 758.
Use CONSTRUCTION A – Internal wiring. CONSTRUCTION B – Internal or external wiring. CONSTRUCTION C – External wiring for Lighting Fixtures.
UL and the UL Logo are trademarks of UL LLC © 2014