APPLIANCE WIRING MATERIAL
Style 2387 Jacketed Cable.
Rating 60 deg C, 30 Vac, Cable flame.
Conductor 40 AWG – 10 AWG solid or stranded round, tinned or bare copper.
Insulation Labeled or complying with Manufacturer’s AWM Procedure.
Assembly Two or more conducts, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductor is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering (Optional) A 6 mil or heavier PVC covering may be extruded over one or more groups of conductors.
Jacket PVC, Dia 1.501-2.500, 110 mils min average, 88 mils minimum at any point.
Standard Appliance Wiring Material UL 758.
Use Internal wiring or external interconnection in Class 2 circuits of computers and electronic equipment.
UL and the UL Logo are trademarks of UL LLC © 2014