APPLIANCE WIRING MATERIAL
Style 2385 Multiple-conductor cable using non-integral jacket.
Rating 60 deg C, 30 Vac, Cable flame.
Insulated Conductor 40 AWG minimum. Labeled or complying with manufacturer’s AWM procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductor is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional, extruded PVC, 6 mils minimum thickness at any point, over conductor assembly.
Jacket Extruded PVC.
Diameter of core assembly under jacket* Minimum average thickness Minimum thickness at any point
0.700 inch or less 60 mils 48 mils
* – Major diameter if cable is flat or oval.
Standard Appliance Wiring Material UL 758.
Use Internal or external wiring in Class 2 circuits of electronic equipment.
UL and the UL Logo are trademarks of UL LLC © 2014