APPLIANCE WIRING MATERIAL
Style 2384 Multiple-conductor cable using non-integral jacket
Rating 60 deg C, 30 Vac, Cable flame.
Insulated Conductor 40 AWG minimum. Labeled or complying with manufacturer’s AWM procedure.
Assembly Two or more insulated conductors, twisted pairs or groups of twisted insulated conductors twisted together. The insulated conductors or groups of insulated conductors may be laid parallel forming a flat, oval or round cable. The lay of the insulated conductors is not specified. Barrier layers, binders over groups of conductors and/or the complete conductor assembly and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional, extruded PVC, 6 mils minimum thickness at any point, over one or more groups of insulated conductors.
Shield Optional, over one or more groups of insulated conductors and/or the complete conductor assembly.
Jacket Extruded PVC.
Diameter of core assembly under jacket* Minimum average thickness Minimum thickness at any point
0.425 inch or less 30 mils 24 mils
0.426-0.700 inch 45 mils 36 mils
0.701-1.000 inch 60 mils 48 mils
1.000-1.500 inch 80 mils 64 mils
1.501-2.500 inch 110 mils 88 mils
2.501 inch and larger 140 mils 112 mils
* – Major diameter if cable is flat or oval.
Standard Appliance Wiring Material UL 758.
Use Internal or external wiring in Class 2 circuits of computers and electronic equipment.
UL and the UL Logo are trademarks of UL LLC © 2014