APPLIANCE WIRING MATERIAL
Style 2343 Jacketed cable.
Rating 80 deg C, voltage rating not specified, Cable flame.
Conductor 30 AWG min, stranded. Labeled or complying with Manufacturer’s AWM procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering Optional A 6 mil or heavier PVC covering may be extruded over the conductor assembly. .
Jacket PVC, Dia 0.700 or less, 60 mils min average, 48 mils minimum at any point.
Standard Appliance Wiring Material UL 758.
Use External interconnection of computers and electronic equipment.
UL and the UL Logo are trademarks of UL LLC © 2014