APPLIANCE WIRING MATERIAL
Style 2117 Multiple-conductor cable using non-integral jacket.
Rating 80 deg C, 600 Vac, Horizontal flame.
Conductor 28 AWG – 9 AWG, solid or stranded.
Insulation Extruded PVC, 30 mils minimum average thickness, 27 mils minimum thickness at any point. Or Labeled or complying with manufacturer’s AWM Procedure.
Assembly Two to ten conductors may be either twisted or parallel. The designation of all styles of individual conductors used in making up the cable assembly shall be available.
Jacket Extruded PVC, 30 mils minimum average thickness, 24 mils minimum thickness at any point.
Standard Appliance Wiring Material UL 758.
Use Internal wiring.
UL and the UL Logo are trademarks of UL LLC © 2014