APPLIANCE WIRING MATERIAL
Style 2095 Multiple-conductor cable using non-integral jacket
Rating 80 deg C, 300 Vac, Horizontal flame.
Conductor 32 AWG minimum, solid or stranded.
Insulated Conductor Labeled or complying with manufacturer’s AWM procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductor is not specified. A barrier layer and/or fillers are optional. May use same or mixed AWG size.
Jacket Extruded PVC.
Diameter of cable under jacket* Minimum average thickness Minimum thickness at any point
0.350 inch or less 15 mils 12 mils
0.351 – 0.700 inch 30 mils 24 mils
0.701-1.000 inch 45 mils 36 mils
1.001-1.500 inch 60 mils 48 mils
*Major diameter if cable is flat or oval.
Standard Appliance Wiring Material UL 758.
Use Internal wiring of electronic equipment and appliances. Tags may indicate the following: “600 volts Peak for Electronic use only”.
UL and the UL Logo are trademarks of UL LLC © 2014