APPLIANCE WIRING MATERIAL
Style 2589 Multiple-conductor cable using non-integral jacket.
Rating 105 deg C, 30 Vac, Cable flame.
Insulation Labeled or complying with Manufacturer’s AWM Procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. May use same or mixed AWG size.
Covering Optional – Extruded PVC, 6 mils minimum over the conductor assembly.
Jacket Extruded PVC
Diameter of core assembly under jacket Minimum average thickness minimum thickness at any point
0.425 inch or less 30 mils 24 mils
0.426-0.700 inch 45 mils 36 mils
0.70-1.000 inch 60 mils 48 mils
1.001-1.500 inch 80 mils 64 mils
Standard Appliance Wiring Material UL 758.
Use External interconnection or internal wiring of electronic equipment.
UL and the UL Logo are trademarks of UL LLC © 2014