APPLIANCE WIRING MATERIAL
Style 2570 Multiple-conductor Cable using Non-Integral Jacket
Rating 80 deg C, 600, 1000 Vac, Cable flame.
Insulated Conductor 40 AWG min., Labeled or complying with Manufacturer’s AWM Procedure.
Assembly Consists of two or more conductors, twisted pairs or groups of twisted conductors twisted together. The conductors or groups of conductors may be laid parallel forming a flat, oval or round cable. The lay of the conductors is not specified. A barrier layer and/or fillers are optional. Manufacturer shall maintain a complete description of each assembly. May use same or mixed AWG size.
Covering (Optional) a 6 mil or heavier PVC covering may be extruded over the conductor assembly.
Jacket Extruded PVC
Diameter of core assembly under jacket Minimum average thickness Minimum thickness at any point
0.700 inch or less 30 mils 24 mils
0.701-1.000 inch 60 mils 48 mils
1.001-1.500 inch 80 mils 64 mils
1.501- 2.500 inch 95 mils 86 mils
2.501 inch and larger 110 mils 94 mils
Standard Appliance Wiring Material UL 758.
Use External interconnection or internal wiring of electronic equipment.
UL and the UL Logo are trademarks of UL LLC © 2014